chiller is dead on water and load lock pump down at normal time. installed spare chiller was originally use for drytek. cb5 breaker on sts was rated for 16amp new chiller rated for 18amp. had to wire rebuild chiller to spare 30amp outlet. chiller temporary not feed by sts remote ac.